Inspect and Repair Steam Traps
Source: U.S. Department of Energy
In steam systems that have not been maintained for 3 to 5 years, between 15% to 30% of the installed steam traps may have failed—thus allowing live steam to escape into the condensate return system. In systems with a regularly scheduled maintenance program, leaking traps should account for less than 5% of the trap population. If your steam distribution system includes more than 500 traps, a steam trap survey will probably reveal significant steam losses.
In a plant where the value of steam is $10.00 per thousand pounds ($10.00/1,000 lb), an inspection program indicates that a trap on a 150-pound-per-square-inch-gauge (psig) steam line is stuck open. The trap orifice is 1/8th inch in diameter. The table shows the estimated steam loss as 75.8 pounds per hour (lb/hr). After the failed trap is repaired, annual savings are:
Annual Savings = 75.8 lb/hr x 8,760 hr/yr x $10.00/1,000 lb
antabuse pills look like human resource research paper why is africa so poor essay 30 years from now essay writing http://hyperbaricnurses.org/8859-find-viagra-free-sites-computer/ canada drug no prescription needed dogs prednisone arthritis https://tffa.org/businessplan/no-talking-in-class-essay/70/ dissertation littraire universitaire cialis eagle see url go site cealis on line il cialis fa durare di pi gay marriage in the united states essay https://themilitaryguide.org/14days/ban-smoking-essay-conclusion-examples/55/ enter site here follow source link cialis cross timber c coles murrmurs essay https://greenechamber.org/blog/communication-research-paper/74/ click here https://companionpetstn.com/medication/book-celeste-cheap-com-guest-levitra-site/32/ can bystolic increase blood sugar essays on the economy case study coffee sandy aristotle political animal essay questions quick forum readtopic viagra none search clamelle walgreens paxil and rage READ THE FULL REPORT (Link to Pdf)